Payment & Shipping Terms:
|Type:||Online Low Frequency Ups||Capacity:||100KVA/80KW|
|Phase:||Three Phase Online Ups||Usage:||Industrial Equipment, Boiler Room,etc|
|Factor:||0.8||Waveform:||Pure Sine Wave|
100kva/80KW full protection online ups isolate transformer 3-phase low frequency UPS
3/3 low frequency ups
small and medium sized data centers,Server,critical network devices, sensitive electronic equipment,small rooms, small precision electronic instrument
b. Functions & Features
1) DSP Technology
2) Superior overload capability
3) Large LCD display and LED indicator
4) 50/60Hz source auto detection
5) Emergency Power Off (EPO)
6) Advanced battery charging management
7) N+X parallel redundancy
8) Fault detection and alarming
9) The efficiency of the machine is more than 93%, and reach 98% in ECO mode.
10) High security dual ac power input function
11) The frequency and phase sequence adaptive system
12) Powerful panel Settings function
13) Intelligent RS485+SNMP+AS400 communication port
|Norminal Voltage||3*380VAC/400VAC(3PH +N)|
|Acceptable voltage range||285VAC~475VAC|
|Waveform||Pure Sine wave|
|Total Harmonic Distortion(THDv)||≤2% (linear load); ≤5% (non-linear load)|
|Phase Displacement||120°±1%(balanced load); 120°±2%(imbalances 50% of the load)|
|Dynamic Recovery Time||3 cycles at 90% of the static value|
|Admissible Overload||110% for 10min;150% for 60sec;>160% for 200ms|
|Admissible Power factor||0.6~1(inductive or capacitive)|
Imbalance output voltage
@100% unbalanced load
|Current limit||High overload, short circuit, RMS voltage limit, High Crest-factor Curren, Peak voltage limit|
|Activation Criterion||Microprocessor control|
|Admissible Overload||150% for 1hour;180% for 30sec;>200% for 200ms|
|Transfer to Bypass||Immediate, for overload above160%|
|Retransfer||Automatic after alarm clear|
|Overall Efficiency(line mode)||Line mode||105%±5% ≤load,warning overload;|
|Battery Mode||105%±5% <load≤125%±5% Transfer to bypass and Alarming after 2 mins;|
|BATTERY & CHARGE|
|Battery type & Number||12VDC*32pcs(29~32pcs adjustable)|
|Normal Battery Voltage||384VDC(Based on 32pcs batteries)|
|Charging Current||Default 10A, Max.=capacity(KW)/battery voltage(real time)||Default 10A, Max.40A;5A@ full load|
|Charging Voltage||432VDC(Based on 32pcs batteries)|
|Safety requirements||GB4943-2001/IEC62040-1 EMC/EMI, IEC 61000-4-5 Protection surge|
The service we can supply:
1.10 years factory, engineers with 15years experience average
2. Supply OEM/ODM service----the logo,color,plugs and sockets,LED/LCD display,USB port,RJ45/11 port, etc.
3.Samples/Small order for testing welcomed.
4.Any customized design is welcomed.
5.1-3 years warranty, provide technical training
6.Provide 365days,7*24hrs hot-line service to user to advisory for the problems of the shangyu service, products, technical, business and fault repair, service Hot-line is 400-0505-800
Why choose Shangyu?
1. 20 years experience engineers
2. 5 years UPS and UPS Battery export experiences
3. 10 years UPS and UPS Battery manufacturer experiences
4. 3 years of high-level OEM Experience
5. 200 Employees.
6. 5,000 square meters Factory Size (Sq.meters)
7. 10,000pcs Monthly Capacity
8. Export Percentage: 50%
9. Hi-tech Advanced R&D Team
10. Certifications--Applied with CE,TCL,ISO 9001,ISO14001 etc
11. 1 years warranty for UPS & UPS Battery.
12. Supply the technology training.
Customers Provide proper instructions to the technical support department through proper procedures to explain the cause and condition of any damage to the product.The detail procedure of warranty as belowing:
1.Send Photo or video of damage products with Serial number label to shangyu,will reply you in 12 hours.
2.The technical engineers will send the Detection table to you for feedback in 24hours.
3.Fault handling and suggestion table will be send to you in 48hours after technical department get the Detection table.
4. We will send you the spare parts by free if the problems caused by us during warranty period.If it is the men-made problems,we also send the spare parts,but you should pay.
5.Other problems can be solved according to the Fault handling and suggestion table.If any misunderstand,call us immediately.